24KW / 30KVA Cummins Engine Powered Diesel Generator AC 3 Phase
- Every generator set is subjected to a comprehensive test program
which includes 25% load, 50% load, 75% load, 100% load, 110% load
and the checking, proving of all control and safety shut-down
- Equipped with battery charger and 24V high performance
maintenance-free lead-acid starting batteries and connecting with
- Equipped with industrial silencer and flexible exhaust hose.
- Equipped with 8-hours operation base tank.
- Equipped with CHNT MCCB circuit breaker.
- Designed to comply with ISO 8528/GB2820.
- Powered by Cummins engine and coupled with Stamford alternator.
|Genset rated power||24KW / 30KVA|
|Rated voltage||240V / 415V (adjustable)|
|Rated current||42 Amps|
|Power factor||0.8 Lagging|
|Connecting type||3 phase 4 wire|
|Cooling system||Closed cycle water-cooled with fan, water tank|
|Overall dimension (L×W×H) mm||1800×800×1200|
|Engine structure||4 cylinders vertical in line, 4 stroke, turbocharged|
|Rotating speed||1500 RPM|
|Engine cooling method||Water-cooled|
|Speed governing system||Electronic speed governor|
|Starting method||By 24V batteries|
|Engine filter system||Dry type air filter ,fuel filter, oil filter, water filter|
|Compression ratio||16.5: 1|
|100% Load fuel consumption (litre/h)||≤6.0|
|Excite type||Brushless self-excited AVR regulation|
|Connecting type||3 phase 4 pole|
|Steady frequency change||0.50%|
|No load voltage||≥95%-105%|
|Insulation class||Class H|
- Control, monitor and protect the Generator Set including:
- High water temperature
- Low oil pressure
- Over and under speed
- Over current
- Under/Over generator voltage
- Start and stop failure
- Low and high battery voltage
- Charge fail
- Emergency stop
INSPECTION AND TEST
1.1 Each engine shall be tested at manufacturer’s workshop to
certify the engine output and fuel consumption in accordance with
the site operating condition specified by purchaser on the
1.2 All relevant information drawings pertinent to the testing and
test procedure shall be transmitted to the purchaser in advance of
the test date notification.
1.3 The purchaser shall call for additional testing if test results
are unsatisfactory or marginal. Any equipment rejected shall be
repaired or replaced to the purchaser’s satisfaction and tests
shall be repeated.
1.4 Any unsatisfactory material, equipment, installation, or
workmanship shall be replaced or repaired to the purchasers
satisfaction at the manufacturers cost.
1.5 The engine and generator shall be tested individually in
accordance with relevant standards specified above.
1.6 The completed and individually tested engine and generator
shall be assembled onto the base plate with all auxiliaries,
instruments and controls for a complete test of the generator set.